Ideal Logic Combi Boiler L2 Error Code
Today I had a callout to a boiler repair in Dartford. It was an Ideal Logic Combi boiler showing an L2 fault and it wouldn’t reset.
An L2 fault code means there is an ignition problem with the boiler.
There are several components that can cause an L2 fault including:
- Flame sensor
- Spark generator
- Gas valve
- Spark electrode
… to name the most common.
Get Your L2 Fault Repaired For A Fixed Price
Call today to get your L2 fault assessed for FREE and repaired for a very reasonable fixed price, which includes a 12 month warranty.Call For Free Assessment
After carrying out some diagnostic work, I traced the problem to the spark generator. It wasn’t creating the spark needed to light the boiler, which was causing the L2 fault.
I replaced it and the boiler was back to working as normal.
How much does an L2 fault code cost to fix?
It depends on the company you deal with and their rates.
But as a rough idea, this spark generator should be about £35 at the time of writing.
Labour should be no more than an hour to install, plus any call out/diagnosis charge.
What does it look like?
Here’s a picture of the spark generator I replaced:
So if you have a similar fault, please get in touch and I’ll do my best to help you!
Are you a heating engineer?
Chances are you’ve found this page because it was high up on Google.
This wasn’t a lucky mistake. I did this on purpose and it’s paying off.
Like you, I’m always looking for better, cheaper ways to get work. Ranking high on Google for the right keywords is a great way to do this – and something I’ve learned how to do myself.
I’m starting to do this for other businesses as well as mine.
So if you’d like me to help you get your website showing up on the search engines, please drop me an email – firstname.lastname@example.org.